TEPCO has completed work to address the leakage of contaminated reactor water into the main building for unit 3. Raised cooling water levels in containment were found to have caused new leaks into the MSIV room outside of containment. A floor drain nearby had been directing this contaminated water into a corner area in the torus room basement. When the floor drain clogged this highly radioactive water leaked further across the first floor of the building.
A hole was drilled into the floor to force the contaminated water to directly flow into the torus room where it can be collected and pumped out along with other contaminated water that flows into the basement. Water that had flowed into other parts of the basement was then pumped out.
The high radiation levels in this water along with notable amounts of alpha radiation and TEPCO’s admission that the alpha radiation is in fine particulate. is indicative of fine fuel particles leaking out along with the water. TEPCO’s efforts to manage this water shows they considered it a serious problem.
Some of the contaminated water flowed down the stairs in the southeast corner of the building.
The hole should help better contain the problem and prevent the contaminated water from finding more direct routes out of the building. TEPCO currently has no plan for blocking the containment leak in the MSIV room, mainly due to the radiation levels in the vicinity.
Machine translated document:
This article would not be possible without the extensive efforts of the SimplyInfo research team
Join the conversation at chat.simplyinfo.org
© 2011-2021 SimplyInfo.org, Fukuleaks.org All Rights Reserved Content cited, quoted etc. from other sources is under the respective rights of that content owner. If you are viewing this page on any website other than http://www.simplyinfo.org (or http://www.fukuleaks.org) it may be plagiarized, please let us know. If you wish to reproduce any of our content in full or in more than a phrase or quote, please contact us first to obtain permission.